This page contains our notes about our proposed solar PV and air source heat pump installation.
- Solar Photovoltaic (PV) System
- Air Source Heat Pump (ASHP) System
- Control and Monitoring
- Installer-specific notes page (password protected): Solar PV & Heat Pump: installer info
Our Household Energy Usage History
year Elec kWh Gas kWh 2018 4,500 16,000 2019 4,500 16,000 2020 5,500 16,000 2021 5,500 17,000 2022 4,500 13,000 expected ~5,000 ~16,000?
- Years based on October to October billing. 2018/2019 are a 2-year average (2019 bill unavailable).
- Why is our 2022 gas usage low? Were we so frugal? Was weather so mild?
Solar PV System
Our own roof measurements
- 4 potentially useful roof surfaces
- 2 larger roofs roughly south facing:
- roof pitch: 45°
- roof azimuth: 20° east of south (compass bearing 160°)
- roof height: 27~30 tile rows
- 2 smaller roofs roughly east facing:
- roof pitch: 45°
- roof azimuth: 20° north of east (compass bearing 070°)
- roof height: 27~30 tile rows
Our own system planning exploration
- Easy PV Project Report – Julian’s version 1
- This plan is only illustrative, for discussion; not verified, not complete, not final.
- We have no preference for make and model of the panels, other than obviously preferring higher output, all else being equal.
- This version of our plan shows a 6 kW inverter where 5 kW is probably enough; likewise other details may be inappropriate.
- No shading is defined for any panels in this version. In reality some shading is likely.
- This version of our plan shows panels that are slightly more elongated than usual, 1855 x 1029 mm (Jinko Tiger 410W N-Type Black Framed Mono). This type is shown just to illustrate one of the extremes of shape that might fit. The same pattern could work using any of the more common panel sizes around 1100×1700 mm, if sufficient top-to-bottom measurement is available on the roofs.
It’s currently looking to me like sixteen panels may be too much of a squeeze. Also, on the two more north-westerly roofs, the lower they reach the more shading they have.
Aim: local home automation connection; avoid depending on manufacturer’s “cloud” service.
Tech specs relevant to solar inverters:
- Communication protocol: (standard) SunSpec Modbus protocol IEEE-1547 (explanation), (optional) manufacturer’s other open protocol such as Fronius API (JSON).
- Communication physical connection: any of Ethernet, WiFi, Zigbee, perhaps other.
- Fronius seem to be the only inverter manufacturer that makes known a serious commitment to local API with open protocols: Fronius Solar API info.
- Home Assistant (preferred open home automation system) has good integration for Fronius inverters.
- SolarEdge looks like the second best make in this regard: local connection available through hard-wired ethernet (previously also wifi but that no longer enabled in recent versions).
- Home Assistant has some integration for local connection to SolarEdge and a few others; but neither SolarEdge nor others seem to promote or prioritise this from their end.
- Fronius Primo GEN24 Plus (page for installers | page for home owners)
- probably 5.0 kW (available models: 3 to 6 kW)
- with “full backup” add-on, because “why not?”: small additional cost for grid outage backup.
Some suppliers of Fronius Primo GEN24 Plus (just from a general DuckDuckGo search):
- Wind & Sun Ltd. ~£2000, +44 (0)1568 720364, email@example.com
- Bimble Solar ~£2000, +44(0)1273 931110, firstname.lastname@example.org
- SolarAnna Ltd. (ZEROhomebills.com) ~£1800, +44 (0)333 7720526,
Assigning strings of panels to MPP Tracker inputs:
- There are 4 potentially useful roof areas, two roughly south facing (-20°, or SSE), two roughly east facing (-110°, or ENE).
- The two more north-westerly roofs will have some shading from the more south-easterly roofs, at times of low sun elevation. If this is significant, do we need to consider dual inverters to give each group of panels its own MPPT input? That is “option B”.
- Option A: 1 x Fronius Primo GEN24 Plus 5.0 kW, with 2 MPPT inputs: all south-facing panels (10) to one, all east-facing panels (6) to the other.
- Option B: 2 x Fronius Primo GEN24 Plus 3.0 kW, total 4 MPPT inputs: each group of panels to a separate MPPT input (5 south, 5 south, 3 east, 3 east).
Aim: maximise capacity, for the sake of future use and economy of scale.
- No particular requirements on size, make, style, colour.
- See my plan (shown above) made on Easy-PV
- Consider whether 16 panels can fit.
- Consider panels of more elongated shape (~1850 x 1050 mm) instead of the more common shape (~1700 x 1100 mm) if that helps.
- Considered triangular panels: they seem to be expensive and hard to obtain (few suppliers).
- Lichen growth, especially on non-south-facing panels. Are some panel types more resistant than others? Concern because ours are quite high and difficult for cleaners to reach.
- Battery sizing. Still TBC whether we install PV + ASHP together or PV first and ASHP later. Consider probably sizing for PV + ASHP. (Is that the conditions where a smaller battery is appropriate?)
- Battery and inverter in under-stair cupboard next to existing electric supply consumer unit.
Air Source Heat Pump (ASHP) System
- Considering east-facing chimney breast above garage, at north-east corner of house. Discussed with surveyor. Ideal siting for connection to existing heating pipes in garage below, and access is good. It’s a potential bedroom, so vibration is a concern, but it’s old solid walls.
Aim: upgrade to better control than simple whole-house thermostat and time switch.
- controlled from smart TRVs? (related to “zoned” control?)
- general introduction: https://www.theheatinghub.co.uk/best-smart-heating-controls-compatibility-guide
- standards: OpenTherm?
- compatibility: ???
- Replace existing simple time switch with new controller (TBD).
- How suitable is ASHP with zoned heating in an old house? Podcast to listen to: The Multi-Zone Heat Pump Issue (greenbuildingadvisor.com)
Other Installation Requests
- Remove gas boiler flue completely and make good the roof. (Check: do we have spare tiles?) Aim: weatherproof.
- Remove excess pipe runs from old boiler location in garage: route directly to new ASHP location. Aim: tidiness.
- Site the hot tank for shortest possible outlet pipe run to domestic hot water supply. That would be south-west corner of garage. Aim: minimise time delay and waste in using domestic hot water.
Control and Monitoring
Open source home automation system:
- Home Assistant: see my article A Freedom-Respecting Smart Home
- Home Assistant’s page on Home Energy Management
- OpenEnergyMonitor project; their shop; their EmonCMS which can be self-hostd
Solar PV monitoring:
Heat pump monitoring: